How To Maintain A Water Heater and Keep it Running Efficiently
Category : Plumbing Problems
This particular water heater maintenance information will provide you with the tools for making your heating unit last much longer. As with everything else, the more you look after it the more time it is going to last. We shall start with a glance at the storage type units’ routine maintenance.
Once you warm the water in the tank, lots of minerals, as well as things, emerge from the water. It is referred to as sediment since it forms out of the water. While this sediment accumulates, it does make it more difficult to transfer the warmth to the water. This may lead to less effective heater operation as well as quick tank failure. Section of the maintenance process will be the eradication of this residue. It is achieved by doing a drain and flush of the heating unit. This ought to be conducted at least once each year.
You need to begin by blocking the supply of the oil, gas, and/or electricity to the heater. There exists a drain valve at the base of the tank. You need to connect a garden hose with it and also run it to a sump. At this point, turn off the supply of cold water to the heater and then the drain valve must be opened up. You must also open a hot water tap to aid the system to drain.
As soon as the water ceases to drain, you need to turn off the hot water tap. After that, turn on the supply of cold water and allow the water to flush out your tank.
Once the water becomes clear, close the valve and also detach the hose. Fill up the tank and next turn on the oil, gas, and/or electricity.
An additional section of the annual water heater maintenance must be checking out the functioning of the relief valve. It is actually a safety feature which helps prevent the tank from getting over pressurized. This safety valve must have a pipe attached to it and also be extended down near to the floor. This pipe needs to be the exact same size as the relief valve’s outlet.
For testing the valve, start by putting a pan beneath the relief pipe for catching the water. You will find a small lever above the relief which is employed to activate it physically. The lever has to be pulled up and you must make sure that the water runs via the pipe. The lever has to be pushed back down and also the water must stop.
As soon as the pipe dries, it is possible to get rid of the pan. Now you can be certain that the valve is going to work.
Water heater maintenance must also consist of checking for indications of leakage. No water should be close to the tank or even its attached piping. Any signs of water must be looked into and fixed as quickly as feasible to prevent any damage to property.
The anode rod should be inspected at least every 3 years. The regularity of replacement is going to vary with the quality of the local water. To examine the rod, start by draining your tank in line with the annual procedure. After that, you may remove the rod after unscrewing it. If the majority of the anode rod is no more than 5/8 of 1 inch in diameter or maybe the support wires are noticeable, the rod must be changed. After the assessment, you may mount the rod back in your tank. After that finish the process of flush and fill. The relief valve also needs to be examined as above.